Rinse and trial transportation of raw water heater
The rinse of the raw water heater was washed and suppressed in the entrance tube; the body was washed, suppressed, and exported tube was washed and suppressed. The manufacturer of scale removable agent suggested that the water heating device first rinse it first, and after the suppression is qualified, the branch can be trial operation.
(1) When starting the water heating device of the raw water heater, it should follow the operation order of the first water and then rear valls:
① Open the water-water heating device with water entrance door and air door, fully exhaust, and close the air door after the water door is out of water.
② Open the water gate and air door of the soda heater, and close it after the air door is out of the water.
③ Open the water-water heating device hydrophobic doors and steam-water heater hydrophilic doors in order.
④ The manufacturer of scale removal agent recommends slowly opening the water-water heating device steam entrance door to put the raw water heater into operation.
(2) The trial operation of the raw water heater
① When running the water heater, control the water outlet temperature of the heater is 30 ~ 35 ° C. If the temperature fluctuates or does not meet the requirements, it should be adjusted in time. Within the range.
② Pay attention to the operation of the heating device during operation. The water dredging door is appropriate. The water level of the hydrophobic tank is maintained at more than 1/2, and the number of operating tables for water pumps is reasonably determined according to the changes in the water level of the hydrophobic tank.
③ The manufacturer of scale removal agent recommends that when two or more heater runs parallel, the operating load of each heater should be reasonably distributed.
Product Recommendation: Sparge Water Heater